Design and Simulation of Wind Pump System for Ban Village
|International Journal of Engineering Trends and Technology (IJETT)||
|© 2016 by IJETT Journal|
|Year of Publication : 2016|
|Authors : Maren I. Borok, Zwalnan, S. Johnson, Agontu J. Agandu
|DOI : 10.14445/22315381/IJETT-V35P217|
Maren I. Borok, Zwalnan, S. Johnson, Agontu J. Agandu"Design and Simulation of Wind Pump System for Ban Village", International Journal of Engineering Trends and Technology (IJETT), V35(2),80-84 May 2016. ISSN:2231-5381. www.ijettjournal.org. published by seventh sense research group
The significance of water to human existence can never be overemphasized. Most rural areas do not have access to portable drinking water. Underground water has been adjudged by World Health Organization (WHO) to be a relatively better alternative source of portable drinking water. Hand pump may not provide adequate water for larger community; diesel engine pump emits Green House Gases (GHG). Thus a relatively better alternative source of energy is the wind. Wind pump is designed for Ban village to pump water from borehole to an overhead tank to be supplied to the village, since Ban village is considered to be one of the locations in Nigeria that has high wind speed that can be harnessed for wind pump technology. Design results show that a 3.6 m diameter wind mill will be required to pump water from borehole through a total head of 35 m to the village to meet the daily water need of 25 m3. Results from the Wind Energy Resources Analysis (WERA) software simulation using the wind speed characteristics of the region shows that the monthly water discharge by wind pump is proportional to the monthly average wind speed with the peak monthly discharge of about 3000 m3 in January which declines to about 1,000 m3 in October. This volume of water is enough to meet the monthly water need of the village.
 H. I. Ajaegbu,Jos Plateau Environmental Resources Development, Plateau, Nigeria: Jos University, Press, 1992.
 N, Argaw, R. Foster and A. Ellis, Renewable Energy for Water Pumping Applications in RuralVillages Period of Performance, New Mexico State University: NREL, 2001.
 J. D. Burton andA. E. Pinilla“Water pump for wind mills – A comparison between two commerciallyavailable systems from South America”. Wind Energy. Vol. 9 (1): pp. 50-58, 1985
 J. F. Douglas, J. M. Gasiorek and J.A. Swaffield, Fluid Mechanics,London: Pitman, 1983.
 P. Fraenkel,Water Pumping Devices: A Handbook, UK: I T Publications, 1986.
 A. C. Guyton, Text book of Medical Physiology, 8th ed, Philadelphia: W.B.Sunder, 1991.
 E. Hofkes,Small Community Water Supply. New York: John Wiley and Sons, 1988.
 S. Lancashire,J. Kenna and P. Fraenkel,Wind pumping Handbook , London: International Technology Publications, 1987.
 Longpigrand, “Hydro-geophysical investigation of PW Nigeria Limited Base Camp, Ban village, Heipang, Nigeria” Tech. Rep. 2008.
 E. H. Lysen, Introduction to wind energy,Amersfoort, Netherlands: CWD-Consulting Services Wind Energy Developing Countries, 1983.
 N. Manwell,Hybrid Energy Systems, Encyclopedia of Energy, Elsevier Inc, 2004.
 S. Matthew, Wind Energy, Fundamental, Resource Analysis and Economic, New York: Springer-Verlag, 2006..
 PRUWASSA “Geo-hydrological Analysis Report of Ban village, Heipang, Nigeria” Tech. Rep. 2009
 M. J. Stevensand P. T. Smulders,“Wind Energy” Engineering Journal, vol.2, 1979.
 UNESCO “The Nigerian Observer”of September 9th, 2011.
 J. van Meel and P. Smulders, (1989) “Wind pumping Hand book” , World Bank Technical Paper, 1989.
Wind speed, Wind pump, Simulation.